Hawke CSB 656N Cable Glands
Hawke CSB 656N cable glands are suitable for use with conduit incorporating individual insulated conductors for both indoor and outdoor use.
For particular use with: –
a) Cable inner sheaths that are not effectively filled, compact and/or circular, have tape bedding or have hygroscopic fillers.
b) Cables that exhibit ‘cold flow’ characteristics.
c) Enclosures containing an ignition source in gas group IIC areas or containing an ignition source in a Zone 1 area.
Hawke CSB 656N cable glands are dual certified Exd and Exe and suitable for installation in Zone 1, Zone 2, Zone 21, Zone 22 and in Gas Groups IIA, IIB and IIC.
When used in increased safety applications the Hawke cable gland can be used to terminate braided cables where the braid and the cable outer sheath enter into the electrical enclosure or junction box.
♦ Exdb IIC Gb, Exe IIC Gb, Extb IIIC, Db Non-aromoured Cables ATEX & IECEx Cable Gland.
Hawke CSB 656N cable gland is suitable for cable termination and installation in Zone 1 (21), Zone 2 (22) and Division 2 hazardous areas.
- Flameproof Exdb
- Increased Safety Exeb
- Dust Extb
- Dual Certified Cable Gland For Hazardous Areas ATEX – IECEx
HAWKE CSB 656N CABLE GLAND TECHNICAL SPECIFICATION
- Hazardous Area Cable Gland Classification – Exdb IIC Gb, Exeb IIC Gb, Extb IIIC Db
- Certificate No’s – Baseefa06ATEX0058X and IECEx BAS 06.0015X
- Cable Gland Zone Location – Zone 1, Zone 2, Zone 21, Zone 22 and in Gas Groups IIA, IIB and IIC
- Construction and Test Standards – IEC/EN 60079-0, IEC/EN 60079-1, IEC/EN 60079-7 and IEC/EN 60079-31
- Ingress Protection – IP66, IP67 and IP 68 (30 metres for 7 days) to IEC/EN 60529 and NEMA 4X
- Deluge Protection – DTS01
- Operating Temperature Range -60°C to +80°C
CABLE GLAND SELECTION TABLE FOR HAWKE CSB 656N
|Hawke Size Ref.||Male Entry Thread Size||Female Entry Thread Size||Inner Sheath/ Cores||‘G’ Compressed Length||Hexagon Dimensions|
|Metric||NPT *||Metric||NPT *||‘D’ Max. Over Cores||‘E’ Max. Inner Sheath||NOTE 1 Max. No. Of Cores||NOTE 2 Max. No. Of Cores||Across Flats||Across Corners|
All dimensions in millimetres (except * where dimensions are in inches).
Metric entry threads are 1.5mm pitch as standard.
† Smaller value is applicable when selecting reduced NPT male entry option.
Hexagon dimensions as shown may alter.
Note 1: ATEX/IECEx certification.
Note 2: All other certification.
➡ Cembre cable lugs available to crimp and terminate cable conductors to ensure complete termination of cable.
CABLE GLAND MATERIAL & FINISH
Hawke CSB 656N cable glands are manufactured in Brass (standard), Nickel Plated Brass, 316 Stainless Steel or Aluminium. Brass NPT entries are nickel plated as standard.
PREPARING CABLE & GLAND FOR INSTALLING HAWKE CSB 656N
Pull sufficient length ‘I’ of conductors through the conduit to suit equipment.
CABLE GLAND PREPARATION
Pass sub-assembly parts (1) and (2) over the conductors and start to thread onto conduit, then using a spanner/wrench tighten the sub-assembly of parts (1) and (2) firmly onto the conduit.
Spread the conductors out for the compound packing. Pack the compound between the conductors as shown.
➡ Click Hawke Cable Glands to view the complete range of hazardous area glands certified according to ATEX & IECEx for Zone 1 / Zone 2.