Ellis Patents 1FP-21SS 65-74mm Fireproof Cable Cleat
ELLIS CABLE CLEATS
Single Cable Cleats
Cable Cleat Maximum Short Circuit Test Level 60kA – Cleat Spacing 600mm
Ellis 1FP-21SS Ellis Patents Phoenix cable cleats are designed for the installation of Fire Protection (FP) rated cables – the fireproof cleats are manufactured from stainless steel, easy to fit and are corrosion resistant – suitable for LV (Low Voltage), MV (Medium Voltage) and HV (High Voltage) power cable circuits.
Phoenix Cable Cleats form part of the Ellis Patents range of fireproof rated cable cleats.
Cleats tested to BS 8491:2008 and BS 5839-1: 2002, section 26.2d.
Ellis Cable Cleat 1FP-21SS
- Cable Cleat Diameter Min 65mm
- Cable Cleat Diameter Max 74mm
Ellis patents 1FP-21SS Cleat Dimensions
- H 82mm
- W 98mm
- D 40mm
- E 13.7mm
- Weight 293g
SINGLE CABLE CLEAT SELECTION TABLE
Specification details for Ellis Patents Phoenix 1FP-21SS cable cleat for single cable applications:
|Phoenix Cable Cleat Part Number||Min Dia (mm)||Max Dia (mm)||H (mm)||W (mm)||D (mm)||E (mm)||Cleat Fixing Holes||Weight (g)|
|1FP-21SS||65||74||82||98||40||13.7||1 x M10||293|
Phoenix CABLE CLEATS – INSTALLATION INSTRUCTIONS
Installation instructions for single way cables using Phoenix cable cleats manufactured by Ellis Patents:
|1. Position the cable clamp and fixing (not supplied) onto the support structure||2. Install the cable||3. Locate the other half of the cable clamp. Secure a nut and washer (not supplied) to the support structure and tighten||4. Important – Do not over tighten the clamp. The clamp should secure the cable but does not need to be so tight that the cable bulges at either side of the clamp or becomes angled excessively.|
Fire Resistant Cables & Cleats
Fire resistant cables and accessories including cable joints, glands and cleats ensure continued operation of armoured power cables in emergency and essential building service systems in the event of fire.