Ellis Patents Phoenix Cable Cleats – Fireproof & Fire Rated
Phoenix Cable Cleats
Single Cable Cleats
- Manufactured By Ellis Patents
- Maximum Short Circuit Test Level 60kA
- Cable Cleat Spacing – 600mm
- Cable Cleat Type – Single Cables
- Material – Stainless Steel
- Cleat Range Single Cables – 10-74mm
Thorne & Derrick International, based in the UK, stock and distribute the complete range of cable cleats and cable hangers manufactured by Ellis Patents including the Phoenix range for short circuit retention and cable protection of LV (Low Voltage), MV (Medium Voltage) and HV (High Voltage) power cable systems in single-way installation.
Ellis Patents Phoenix cable cleats are fireproof rated cable cleats for cable diameters ranging from 10mm to 74mm suitable for single cables. Phoenix cable cleats are manufactured from stainless steel with a single bolt fixing and are available in 12 sizes.
These cable cleats are specifically designed for the installation of Fire Protection (FP) rated cables as they are easy to fit, corrosion resistant and fireproof. To prove their fire resistance these cleats were used to secure a fire rated cable during a series of tests in accordance with BS 5839-1:2002, Section 26.2d.
International Standard IEC 61914:2009
Ellis Patent cable cleats with international specifications are used to clamp and retain LV MV HV cables including 11kV and 33kV networks depending on short-circuit calculations according to IEC61914 calculations.
For cable installations where corrosion protection is required, including onshore and offshore substations or hazardous area locations, see our complete range of ➡ stainless steel cable cleats.
Ellis Patents Phoenix Cable Cleats
Maximum Short Circuit Test Level Cleat Spacing
- 60kA 600mm Cleat Spacing
Installing Cable Cleats
Installation instructions for single way cables using Phoenix cleats manufactured by Ellis Patents:
|1. Position the cable clamp and fixing (not supplied) onto the support structure||2. Install the cable||3. Locate the other half of the cable clamp. Secure a nut and washer (not supplied) to the support structure and tighten||4. Important – Do not over tighten the clamp. The clamp should secure the cable but does not need to be so tight that the cable bulges at either side of the clamp or becomes angled excessively|
Ellis patents Phoenix Cable Cleat Testing Information
Should you require test samples or further specification details about Phoenix cable cleats please contact us:
|Properties||BS EN 50368:2003 Classification Clause||Units / Classification||Phoenix Single Cable Cleat Application Test Data|
|Temperature For Permanent Application||6.2||°C||-40 – 60|
|Corrosion Resistance||22.214.171.124||High||316L Stainless Steel
Has 16% Chromium
|Flame Propagation Test||10.0, 10.1||No Contribution Yo Fire||Metallic|
|Axial Load Rating||6.4.3, 9.4||Newtons (N)||45|
|Lateral Load Rating||6.4.2, 9.3||Newtons (N)||Horizontal – 350N
|Resistance To Electromechanical Force
(Short Circuit Testing)
|6.4, 6.4.5, 9.5||Cleats at 300mm intervals
(Withstand More Than One
|31kA (Report No. PDL‑17.137.1)
Cable OD= Ø36mm
Phase Spacing = 100mm
Phoenix Cable Cleat – Single Cable Application Selection Table
➡ The following selection table provides information to enable the specification or purchase of the correct Phoenix cable cleat – contact Thorne & Derrick for further technical information, installation advice, samples or to place an order.
|Phoenix Cable Cleat Part Number||Min Dia (mm)||Max Dia (mm)||H (mm)||W (mm)||D (mm)||E (mm)||Cleat Fixing Holes||Weight (g)|
|1FP-10SS||10||13||21||40||40||13.7||1 x M10||91|
|1FP-11SS||13||16||24||44||40||13.7||1 x M10||106|
|1FP-12SS||16||19||27||47||40||13.7||1 x M10||114|
|1FP-13SS||19||23||31||51||40||13.7||1 x M10||126|
|1FP-14SS||23||27||35||55||40||13.7||1 x M10||140|
|1FP-15SS||27||32||40||60||40||13.7||1 x M10||155|
|1FP-16SS||32||38||46||66||40||13.7||1 x M10||176|
|1FP-17SS||38||46||54||74||40||13.7||1 x M10||202|
|1FP-18SS||46||51||59||80||40||13.7||1 x M10||225|
|1FP-19SS||51||57||64||85||40||13.7||1 x M10||245|
|1FP-20SS||57||65||73||93||40||13.7||1 x M10||265|
|1FP-21SS||65||74||82||98||40||13.7||1 x M10||293|
Cable Cleats v Cable Ties
The Video produced by Ellis Patents provides compelling evidence of the need to ensure all cables are adequately supported and retained to cable containment to protect against the devastating effects of short circuit faults: 118kA Short Circuit Fault Current | 0.1 Seconds Duration | 480V Low Voltage Cables.