6.6kV 7.2kV Cable Termination Kits 3 Core 150-240sqmm SPS 3TES-7.2X-C
6.6kV cable termination kits using heat shrink technology are suitable for terminating medium/high voltage (MV-HV) 3 core polymeric cables (XLPE EPR) – this includes cables with copper wire/tape screen and armoured (wire armoured/braided) or unarmoured cable for outdoor termination of 6.6kV cables, indoor version also available.
SPS 3TES-7.2X-C cable termination kit suits 6.6kV 7.2kV cables with 150sqmm, 185sqmm, 240sqmm 3 core conductors – outdoor cable terminations can be supplied with stand off insulators, surge arresters, crucifix cable support bracket and cable cleats.
6.6kV 7.2kV Cable Termination
HV High Voltage – Outdoor
- Cable Termination Type – Heat Shrink
- Termination Location – Outdoor (Pole Moutnted)
- Number of Cores – 3 Core
- Conductors – 150sqmm, 185sqmm, 240sqmm
- Cable Type – XLPE EPR (Polymeric)
- Heat Shrink Standard Tail Length – 700mm
- Termination Kit Order Code – SPS 3TES-7.2X-C
- Suit MV HV Power Cables – BS6622, BS7835, BS7870, BS6883, BS7917 & IEC60502-2
HV Electrical Safety
Electrical safety equipment enables the safe construction and maintenance of MV HV Power Networks including overhead line conductors and underground power cables – this includes 6.6kV, 11kV and 33kV networks.
A full supporting range of arc flash clothing is available to protect jointers and linesmen from the dangers of electrocution and insulating gloves for hand protection when working on or around live electricity networks.
Outdoor Cable Terminations 6.6kV
3 Core XLPE
The following enables the termination kit selection for 6.6kV 3 core outdoor cables:
|6.6kV/7.2kV 3 Core Cable Termination Indoor||Heat Shrink Cable Termination Kit Range||6.6kV/7.2kV 3 Core Cable Termination Outdoor|
Earthing Outdoor Cable Terminations With Surge Arresters
Engineering standard vary locally and internationally, however UKPN a distribution network operator supplying electricity covering South East England, the East of England and London recommend the following earthing system for pole-mounted cable terminations – the main HV earth conductor shall be connected from the pole-top steelwork to an HV underground copper earth rod located at the bottom of the pole.