BS6622 – 6.35/11kV Single Core AWA Cable
Nexans Cable Description: Single core armoured cable with XLPE insulation. Rated voltage 6.35/11 KV
International : IEC 60502-2
National : BS 6622
Description: BS6622 11kV medium voltage electric power cable with copper conductors, semi-conductive conductor screen, XLPE insulation, semi-conductive insulation screen, copper tape metallic screen, PVC bedding, galvanised steel wire armour (SWA) and PVC outer sheath. The cable is suitable for rated voltage 6/10KV according to IEC 60502-2.
11kV BS6622 Cable Design
1. Copper Conductors
2. Semi-conductive Conductor Screen
3. XLPE Cable Insulation
4. Semi-conductive Insulation Screen
5. Metallic Copper Tape Screen
6. PVC Cable Bedding
7. Galvanised Steel Wires Armour (SWA)
8. PVC Outer Cable Sheath
♦ See Cable Jointing Tools to enable cable sheath, semi-con screen and insulation removal of BS6622 cables.
➡ See HV Cable Joints, Terminations & Connectors to enable the installation of BS6622 6.35/11kV 3 Core SWA Cable – for terminating medium voltage cables into MV-HV gas insulated switchgear, transformers and electrical equipment with outer cone type bushings please see Nexans Euromold connectors – slip-on, heat shrink terminations and cold shrink cable joints from 11kV-33kV (42kV) also available for MV-HV cables.