Ellis Patents 1 Hole Single Cable Clamps
Single Hole Cable Clamps
Single Cable Cleats
- Manufactured By Ellis Patents
- Cable Cleat Type – Single Cables
- Material – Aluminium
- Cleat Range Single Cables – 10-57mm
Thorne & Derrick International, based in the UK, stock the complete range of cable cleats and cable hangers manufactured by Ellis Patents including Single Hole cleats for short circuit retention and cable protection of LV (Low Voltage), MV (Medium Voltage) and HV (High Voltage) cable systems in single-way or trefoil installation.
Ellis Patents Single Hole cable clamps are stainless steel single cable cleats for cable diameters ranging from 10-57mm – these 1 hole cleats are typically used to clamp and support LV low voltage power cables 600/1000V (BS5467 | BS6724 XLPE SWA Armoured) to cable containment.
Ellis Patents 1 Hole aluminium cable clamps are designed to fix, retain and support low and high voltage cables and are ideal for use in dry industrial or outdoor unpolluted applications.
Additionally, the aluminium cable cleat can be epoxy coated for use in harsh environments and hazardous areas including sea air conditions (offshore).
The Ellis single hole cable cleats are manufactured from LM6 aluminium to BS 1490 and are available in 10 different sizes to suit cable diameters from 10-57mm.
International Standard IEC 61914:2009
Ellis Patent cable cleats with international specifications are used to clamp and retain LV MV HV cables including 11kV and 33kV networks depending on short-circuit calculations according to IEC61914 calculations.
For cable installations where corrosion protection is required, including onshore and offshore substations or hazardous area locations, see our complete range of ➡ stainless steel cable cleats.
Installing Cable Cleats
Installation instructions for single way cables using 1 hole aluminium cable cleats manufactured by Ellis Patents:
|1. Position the cable clamp and the 2 screws (not supplied) on the stand||2. Install the cable||3. Place the other half of the clamp. Secure with 1 screw and 1 washer (not provided) and tighten||4. Do not overtighten the cable clamp. The clamp must be in contact with the cable but it does not have to be so tight that the cable is bulging each side of the lining|
Ellis Patents 1 Hole Single Cable Clamps Testing Information
Should you require test samples or further specification details about 1 Hole Cable Cleats please contact us:
|Properties||BS EN 61914:2009 Classification Clause||Units / Classification||1 Hole Single Cable Clamp Application Test Data|
|Impact Resistance||6.3.5, 9.2||Very Heavy Classification (6.7kg at 300mm)||Pass|
|Resistance To Electro Mechanical Force||6.4, 6.4.4, 9.5.3||Refer to Ellis Patents for further details||Refer to Ellis Patents for further details|
|Temperature for Permanent Application||6.2||ºC||-40 to +120|
|Needle Flame Test||10.0, 10.1||Application Time (seconds)||> 120|
|Lateral Load Test||9.3||Newtons (N)||4000|
|Axial Movement Test||9.4||Newtons (N)||300|
Ellis Patents 1 hole single CABLE CLamp – Single Cable Application Selection Table
➡ The following selection table provides information to enable the specification or purchase of the correct 1 hole single cable clamp – contact Thorne & Derrick for further technical information, installation advice, samples or to place an order.
|Cable Clamp Part Number||Min Dia (mm)||Max Dia (mm)||W (mm)||H (mm)||D (mm)||E (mm)||Clamp Fixing Holes||Pack Qty||Weight (g)|
|Ellis 1A-10N||10||13||37.8||27.0||41.4||10.2||1 x M10||1||43|
|Ellis 1A-11N||13||16||41.2||30||41.4||10.4||1 x M10||1||52|
|Ellis 1A-12N||16||19||44.3||33.0||41.4||10.7||1 x M10||1||61|
|Ellis 1A-13N||19||23||48.2||36.0||41.4||10.9||1 x M10||1||68|
|Ellis 1A-14N||23||27||52.2||40.0||41.4||11.3||1 x M10||1||78|
|Ellis 1A-15N||27||32||57.1||44.0||41.4||11.6||1 x M10||1||85|
|Ellis 1A-16N||32||38||63.1||49.0||41.4||12.1||1 x M10||1||97|
|Ellis 1A-17N||38||46||71.3||58.0||41.4||12.9||1 x M10||1||121|
|Ellis 1A-18N||46||51||77.3||67.0||41.4||13.5||1 x M10||1||155|
|Ellis 1A-19N||51||57||83.2||72.0||41.4||13.9||1 x M10||1||171|
Cable Cleats v Cable Ties
The Video produced by Ellis Patents provides compelling evidence of the need to ensure all cables are adequately supported and retained to cable containment to protect against the devastating effects of short circuit faults: 118kA Short Circuit Fault Current | 0.1 Seconds Duration | 480V Low Voltage Cables.