Ellis Patents Elite Cable Clamps & Straps – Range Taking Cable Clamps & Straps
Range Taking Cable Clamps & Straps
Elite Cable Clamps & Cable Straps are range taking cable support products manufactured by Ellis Patents and are practical and easy to install – the single cable cleats are suitable for cable diameters ranging from 9.5-52mm with only four sizes of cleats available to cover the cable range.
The Elite cable clamps and straps are manufactured as standard in Black Polypropylene (B) , White Polypropylene (W) or Black Flame Retardant V0 Zero Halogen Phosphorus Free Nylon (LSF Low Smoke Fume).
The cable clamp has a fully releasable strap allowing ease of installation and can be easily be screw fixed to wall, skirting or cable tray. Used to fix power cables in indoor and outdoor applications and the cable clamp is tested in line with EN 50368:2003.
Ellis Patents Elite
Should you require test samples or further specification details about this range of range-taking cable clamps and straps please contact us.
Elite Range Taking cable cleats have been tested in line with the European Standard of ‘Cable Cleats forElectrical Installations’ BS EN 50368:2003.
Typical results are detailed below:
|Properties||BS EN 50368 Classification Clauses||Units / Classification B||Units / Classification LSF||Test Data B||Test Data LSF|
|Cable Cleat Type||6.1, 6.1.2||Non Metallic||Non Metallic||–||–|
|Impact Resistance||6.2,6.2.2, 6.2.5||Medium 0.54kg @ 400mm to Heavy 1.7kgs @ 300mm||Light 0.27kg @ 400mm to Very Heavy 6.7kgs @ 300mm||pass||pass|
|Resistance to Electro Mechanical Force||6.3||Refer to Ellis Patents for further details|
|Temperature for Permanent Application||6.4||oC||oC||-40 to 40||-40 to 60|
|Needle Flame Test||6.5, 10||Application Time (seconds)||Application Time (seconds)||>5||>20|
|Lateral Load Test||9.2||Newtons (N)||Newtons (N)||150||325|
|Axial Movement Test||9.5||Newtons (N)||Newtons (N)||50||50|
Cable Straps & Clamps
➡ The following selection table provides information to enable the specification or purchase of the correct Elite Range Taking Cable Cleats – contact Thorne & Derrick for further technical information, installation advice, samples or to place an order.
|Elite Cable Clamp Part Number||Material Suffix||Cable Range||Cable Cleat Dimensions||Pack Quantity||Weight g|
|Min Dia mm||Max Dia mm||W(max) mm||H mm||D mm||Fixing Hole||B/W||LSF|
|15-1||B,W or LSF||9.5||16.0||27.0||37.0||25.0||1 x M6||100.0||6.0||8.0|
|15-2||B,W or LSF||15.0||25.0||36.0||37.0||32.0||1 x M6||50.0||8.0||10.9|
|15-3||B,W or LSF||23.0||37.0||48.0||48.0||36.0||1 x M6||50.0||15.0||18.1|
|15-4||B,W or LSF||34.0||52.0||63.0||65.0||40.0||1 x M6||25.0||20.0||25.5|
Installation Instructions For Ellis Elite Cable Clamps
Should you require any technical advice or installation guidance on the use of cable cleats please do not hesitate to contact us.
|1. Fix the Elite cable clamp to the support structure, wall or skirting prior to inserting the cable|
|2. Install the cable onto the cleat|
|3. Locate the retaining strap through the aperture at the rear of the cable support, hand tighten the cable strap|
|4. Pass the end of the cable retaining strap through the two legs below the cable support to lock the strap – to release the cable strap use a screw driver to prise open the legs|
Cable Cleats v Cable Ties
The Video produced by Ellis Patents provides compelling evidence of the need to ensure all cables are adequately supported and retained to cable containment to protect against the devastating effects of short circuit faults: 118kA Short Circuit Fault Current | 0.1 Seconds Duration | 480V Low Voltage Cables.